Even if producers have propane contracted at a reasonable rate, the recent spike in propane prices is additional incentive for pork producers to conserve heating energy, says Jay Harmon, Iowa State University extension livestock production systems specialist.
"Often the first idea for saving heating fuel in hog buildings is to add insulation," Harmon says, "However, ventilation management should actually come first because more than 80% of the heat loss in a swine building is due to improper ventilation."
Harmon offers pork producers these tips for conserving propane this winter:
Proper ventilation rate
The goal during colder months is to control moisture and ammonia as much as possible. Underventilating a building will result in poor air quality and may cause health and growth problems with pigs. Conversely, over ventilating by just 20% can increase propane usage by 50%.
In some cases, especially in wean to finish buildings, minimum ventilation fans may be too large, too many fans are used or the percent speed setting may be too high.
If over ventilation is occurring and you are using two fans for minimum ventilation, try turning off one fan and running the remaining one at a higher speed. Monitor air quality to be sure you are providing enough air. The percentage shown in the controller is likely not the percentage of fan capacity so it may take time to find the appropriate setting.
Adjust the temperature
The proper temperature is important for energy efficiency. Observe the pigs to determine their comfort level. If pigs are too cold, they will huddle and pile up when resting. If they're too warm, they will avoid each other. Adjust the temperature so pigs sleep side by side but not in a pile. Just a few degrees difference can save a substantial amount of propane.
Adjust the heater
The controller should be adjusted so that minimum ventilation fan speed never increases while the heater is cycling. If the heater runs, then shuts down and you can hear a fan increase its speed, it means that the heater is shutting off too close to the setpoint. If you hear this happening, simply adjust the heater to shut off at a slightly lower temperature. In the case of one producer, it was documented that setting the heater to shut off one-half degree lower saved 3.75 gallons of LP per furnace per day.
Adjust the ventilation when using brooders
Some producers use brooders for small pigs. This allows them to keep the room cool, but the pigs feel warmer due to localized heating. If the setpoint is low, for instance 70 degrees, extra fans may switch on to maintain this cool temperature in the room. A better approach is to set the room setpoint just above the brooder temperature, 85 degrees for example, but to have your heater turn off at a lower temperature, such as 70 degrees. By preventing fans from cycling too early, this technique retains more heat in the building rather than discarding it through the ventilation system.
Air leaks such as holes in ventilation curtains, leaky fan louvers or cracks around doors may create cold spots, which cause heaters to run longer than necessary. Eliminate these and other leaks to maintain air quality and to reduce propane consumption.
Source: ISU Extension